Example: air traffic controller
Hochiki America Corporation EVAX 25 Specifications subject to change without notice. ENGINEERING SPECIFICATIONS The voice evacuation system shall be EVAX Systems ...
Text of EVAX - 25 Voice Evacuation System
Hochiki America Corporation7051 Village Drive, Suite 100 Buena Park, CA 90621-2268Phone: 714/522-2246 Fax: 714/522-2268Technical Support: 800/845-6692 or latest revision at - 25 Voice Evacuation SystemSpecifications subject to change without notice Clean dead-front construction Digitally recorded automatic voice evacuation(up to 4 minutes of message capacity) 25 Watt bullet-proof amplifier 25 or 70 VRMS field selectable 120 VAC power supply and battery charger Live microphone override of message and tone Analog addressable compatible High reliability, no maintenance, fully supervised Easy installation and operation Natural voice sound recordings Built-in alarm and alert signals Up to 4 minute message capacity Works with 12VDC or 24VDC fire alarm panels Works with analog/addressable andmicroprocessor based fire alarm panels 3 minute message restart on microphone key 24 hour backup with two 12V 7 AHr batteries Made in the USASTANDARD FEATURESPrimary Power120VAC @ VDC Battery Power; Watts @ 25/70 VRMStone and voiceBackbox "W x 18"H x 4"DColorRed/Charcoal GreyThe EVAX 25 operates with any Fire Alarm ControlPanel (FACP), and provides 25 Watts of EVAX 25 includes all necessary features toprovide an effective voice evacuation system. Withthe addition of zone splitters, remote microphonepanels, and expander modules, the EVAX 25 can becustom configured to satisfy the needs of EVAX 25 has its own power supply and batterycharger. Panel must be wired with 120 VAC andstandby batteries digital message repeater (DMR) is built into theEVAX 25. The selection of alarm tone and automaticmessage repeats, as well as the 6 Hour delay of theAC power failure reporting feature are all paging microphone is an integral of the microphone from the panel will causea "Trouble" condition which will be reported locally, aswell as through the EVAX 25 is housed in an attractive surface orsemi-flush mounted backbox, with a hinged and keylocked on LISTINGS 6911-0410:176CaliforniaState FireMarshalS5694Specifications subject to change without America Corporation EVAX 25ENGINEERING SPECIFICATIONSThe voice evacuation system shall be EVAX Systems Series EVAX 25 or approved voice evacuation system shall provide 25 watts signal power and 25 watts voice power, and shall be UL voice evacuation system shall be micro-processor based, and shall contain an integral microphone, 25-Wattaudio amplifier, tone generator, digital message repeater, 120VAC power supply and battery voice evacuation message/signal shall be broadcast until the Fire Alarm Control Panel (FACP) is reset, or untilfire emergency personnel interrupt the broadcast with a manual page. On reset system shall automatically returnto standby (normal operating) secondary message shall be provided which can be triggered by the closure of a contact from either the FACPor from any normally open contact paging microphone (s) will be supported by the system through a supervised circuit. Remote microphone(s) can be mounted up to 5000 feet away from the voice evacuation DIAGRAMSFireAlarmControlPanelFIRESupervi se - Power LimitedStrobe CircuitNAC (Notification Appliance Circuit)Supervise - Power LimitedNACFIREVoice Evacuation Speaker CircuitSupervise - Power LimitedEOLREOLR120VACPowerTransformer**P ower Transformer isbuilt into the EVAX 50Class "A" Speaker Circuit if requiredTB112345 6781234567891011TB2TB387654321TroubleNor malAlarmSystem Status LEDs12 VBattery-+12 VBattery-+1325764813257648ORDERING INFORMATIONModel NumberDescriptionEVAX 2525W Voice Evacuation System, with power supply/battery charger, pagingmicrohpne and digital message repeaterEVAX 25/4Z25W Voice Evacuation System, with 4 Speaker ZoneEVAX 25/8Z25W Voice Evacuation System, with 8 Speaker Zone